A local beach-front pub experienced failure from two of five roof-mounted package heat pumps during the summer months. Our engineer inspected equipment and found the coils were not suitable for beach-front usage and had corroded under salt-spray exposure. We prepared a thermal/HVAC model of the restaurant and found that the installed system was under-designed by about 20%. Our report prioritized several recommendations for the restaurant to undertake with the incorrect package units given first priority.
Estimated Project Value
$50,000 for all upgrades